Portland State University. Department of Electrical and Computer Engineering
Date of Publication
Master of Science (M.S.) in Electrical and Computer Engineering
Electrical and Computer Engineering
Electric power distribution -- Management, Electric transformers, Electric vehicles -- Energy consumption, Dwellings -- Energy consumption
1 online resource (ix, 58 pages)
Installation and utilization of residential distribution transformers has not changed substantially over a long period of time. Utilities typically size their transformers based on a formula that takes into account broadly what types and how many dwellings will be connected.
Most new residential dwellings feature 200 Amp service per household with an anticipated energy demand of under 20,000 kWh per year. Average electrical energy consumption varies from state to state but averages to 11,280 kWh per year. Energy demand is expected to fall into a typical residential load curve that shows increased demand early in the morning, then decreasing during the day and another peak early to late evening. Distribution transformers are sized at the limit of the combined evening peak with the assumption that the transformer has enough thermal mass to absorb short overloads that may occur when concurrent loading situations among multiple dwellings arise. The assumption that concurrent loading is of short duration and the transformer can cool off during the night time has been validated over the years and has become standard practice. This has worked well when dwelling loads follow an averaging scheme and low level of coincidence.
With the arrival of electric vehicles (EV's) this assumption has to be reevaluated. The acquisition of an electric vehicle in a household can drive up energy demand by over 4000 kWh per year. Potentially problematic is the increased capacity of battery packs and the resulting proliferation of Level 2 chargers. The additional load of a single Level 2 charger concurring with the combined evening peak load will push even conservatively sized distribution transformers over their nameplate rating for a substantial amount of time. Additionally, unlike common household appliances of similar power requirements such as ovens or water heaters, a Level 2 battery charger will run at peak power consumption for several hours, and the current drawn by the EVs has very high levels of harmonic distortion. The excessive loading and harmonic profile can potentially result in damaging heat build-up resulting in asset degradation.
In this thesis I present a device and method that monitors pole mounted distribution transformers for overheating, collect and wirelessly upload data and initiate commands to chargers to change output levels from Level 2 to Level 1 or shut down EV charging altogether until the transformer returns into safe operational range.
In Copyright. URI: http://rightsstatements.org/vocab/InC/1.0/ This Item is protected by copyright and/or related rights. You are free to use this Item in any way that is permitted by the copyright and related rights legislation that applies to your use. For other uses you need to obtain permission from the rights-holder(s).
Zumr, Zdenek, "Last Mile Asset Monitoring: Low Cost Rapid Deployment Asset Monitoring" (2014). Dissertations and Theses. Paper 1967.